EcoCable > PV Cable MC4 to T4 Adapter Pair - #10 AWG
Array adapter - MC4 to T4 -10AWG PV wire 1000V MC4 Male (-) to T4 Female (+)
MC4 Female (+) to T4 Male (-)
Adapters are used when trying to join connectors from the module that do not match up with the inverter. All adapters are made with PV-Wire that has an extra layer of insulation for use on ungrounded arrays in conjunction with transformerless inverters. This type of wire is required to meet the 2008 NEC if you are using a transformerless inverter.
Male versus Female
In most electrical industries, connectors are described as “Male” and “Female” but this applies to the metal contacts themselves, not the plastic insulator that houses them. For some manufacturers of solar equipment, such as Amphenol, Tyco connector systems, the housing of the connector pins appear opposite from standard electrical industries.
The male pin has housing with a relatively large opening in the end and the pin itself is recessed within. The female pin has housing that has a long narrow tip that fits into the male housing when they are mated. This appearance is just the opposite of what the terms “Male” and “Female” usually bring to mind and is the biggest source of problems in ordering exactly what you, the customer, needs.
When ordering adapters for your PV cables, it is vital to specify the physical type of connector for each end as well as its polarity.