Midnite Solar 8 String Disconnecting Combiner with Power Supply Board - Rapid Shutdown System
Midnite Solar MNPV16HV-DLTL 4X Disconnecting Combiner, 2 Pole, 2 Channel, 160 amps or 175 amps for busbars and switch.
DLTL is set up for 8 strings in and 2 strings out for Dual MPPT on transformerless
PV Disconnecting Combiners - Birdhouse Compatible
26"L X 24"W X 6"D
The MNPV16HV-DLTL 4X’s red handled is LOCKABLE IN THE OFF POSITION!
8 strings into the combiner with 2 separate 60 amp strings out. Specifically designed for the new dual channel MPPT on the transformer-less inverters. This configuration will break the Positive and Negative of 2 separate 600vdc strings.
The difference between the regular Disco combiner and the DLTL version is that the MNPV16HV-Disco-4X is made for a single 16 string inverter, Two 8 sting inverters or one 8 string transformerless where as the DLTL is set up for 8 strings in and 2 strings out for Dual MPPT on transformerless
- Rapid Shutdown System compliant
- Birdhouse compatible
- Type 4X aluminum enclosure (No Rust)
- Number of Fuse Holders (MNTS) included - 16
- Fuses included
- Current Rating - 120A
- Max. Output Wire Size - 2/0
- Output Circuits - 2
- 90 degree C connections
- 1/2 strain reliefs (MNSR-1000) included
- Meets 2014 NEC 690.12
- See through dead front and color coded bus bar guards
- #6 AWG internal wiring
- Warranty - 5 yrs.
- Listed by ETL for US & Canada
- Made in the USA
- 16 - 1/2" strain reliefs (MNSR-1000)
- 21 - 1/2" NUT MNT 14
- 9 - HOLE PLUG 1/2" NPT (MNHOLE PLUG 1/2)
- 9 - GASKET 1/2"
- One BLUE WRENCH (MNWRENCH)
SMA requested MidNite Solar to design and build these DLTL combiners. There are 8 strings entering the combiner with 2 separate strings out. Specifically designed for the new dual channel MPPT on the transformer-less inverters.