Midnite Solar SMA Master E-Panel
Master e-panel. Three Slave E-Panels and three additional Sunny Island inverters required.
||E-Panel - SMA
|Dimensions (W x H x D)
||45" x 23" x 14"
Master E-Panel for a 18-24KW quad Sunny Island inverter system. The quad system can be off-grid, AC coupled, battery backup grid tie or battery backup. Three Slave E-Panels and three additional Sunny Island inverters required.
This master E-Panel in a quad Sunny Island inverter system includes a 125amp, 120/240vac AC Output/Bypass system, separate 60amp, 120/240vac AC input and output breakers for the Master inverter, 250amp battery breaker with inverter cables, 500amp/50mV shunt, battery negative busbar, AC input and Output busbars, neutral and ground busbars, AC input and output wiring, transition terminals to Slave E-Panels. All breakers are hydraulic-magnetic and rated for continuous duty. Space provided for 6 additional 1/2" wide din rail mount AC or DC breakers and up to 12 3/4" wide panel mount breakers. Knockouts located for battery cables, lightning protection and AC conduit connections.